Water Chiler Installation Instructions-3
Water chiler installation instructions-3
5, check the water tank level of laser chillers .
After the new machine is turned on, the air in the water pipe is drained, and the water level of the water tank is slightly decreased. Observe and record the current water level, and so on, after a period of time, such as the cold water chiller to observe the water level meter, if the water level decreased significantly, it is necessary to check the leakage of water pipes.
6, adjust the thermostat parameters.
The intelligent temperature controller of cw5300 Chillers for Lasers generally do not need to adjust the control parameters, such as really necessary, can refer to the operating conditions and parameter adjustment.